Lighting switch controller
●AC 220V working voltage
●4-way dry contact input
●4-way 20A relay output (with manual switch)
●DC24V, DC12V sensor power supply
1 way sensor access
●1 channel RS485 panel input
The main function is the input of the remote lighting switch, which controls the switch of the lighting circuit. Can run independently or online. The communication interface is RS485, the communication protocol is BACnet MS/TP, the baud rate is 9600~76.8K bps, and the default is 38.4K bps.
Built-in direct controller application
The lighting controller uses an independent Direct Digital Control (DDC) that provides monitoring of the lighting circuit. The controller has the following functions: switch control schedule control mode control.
List of input and output points
|analog point||digital point||analog point||digital point|
Housing The PCL0404 controller is a compact unit according to DIN 43 880 Gr. 1.
Mounting Methods The PCL0404 controller has the following mounting methods:
Installed in standard electrical control box according to DIN 43 880 standard rail
●Wall mounted in protective enclosure
●Installation from the front with standard mounting elements (screws)
AC 220V ±20%
Standard for automatic control of air-conditioning related applications
137mm X 132mm X 57mm (L X W X H)
Device Instance and MAC address are defined by software