Lighting Dimming Controller
●AC 220V working voltage
●4-channel 0-10V dimming output
●DC24V, DC12V sensor power supply1 way sensor access
●1 channel RS485 panel input
The main function is to automatically adjust the brightness of the lighting circuit through the input of the illuminance sensor. Can run independently or online. The communication interface is RS485, the communication protocol is BACnet MS/TP, the baud rate is 9600~76.8K bps, and the default is 38.4K bps.
Built-in direct controller application
The lighting controller uses an independent Direct Digital Control (DDC) that provides monitoring of the lighting circuit. The controller has the following functions: Illumination control schedule control mode control.
List of input and output points
|analog point||digital point||analog point||digital point|
Housing The PCL0404-A controller is a compact unit according to DIN 43 880 Gr. 1.
Installation methods PCL0404-A controller has the following installation methods: Installed in standard electrical control box according to DIN 43 880 standard rail
Wall mounted in protective enclosure
Use standard mounting elements (screws) to mount from the front.
AC 220V ±20%
Standard for automatic control of air-conditioning related applications
137mm X 132mm X 57mm (L X W X H)
Device Instance and MAC address are defined by software
Installation dimension drawing (unit: mm):